EER and SEER both measure the energy efficiency of HVAC devices such as air conditioners and heat pumps.
EER = ‘Energy Efficiency Ratio’ measures energy efficiency at 100% cooling load, 50% humidity, and 95F to 80F temperature difference.
SEER = ‘Seasonal Energy Efficiency Ratio’ measures energy efficiency throughout the summer (June, July, August). We can consider it as a real-time every EER.
Here is a universal EER to SEER converter. Just input the EER rating, and you’ll get the SEER rating. If you need to convert SEER to EER, you can check the SEER to EER converter here.
Inversely, if you have SEER and would like to calculate EER, you can use this SEER to EER calculator.
Here is the EER to SEER chart for some key EER ratings:
The formula of how to convert EER to SEER is:
SEER = (1 × EER100% + 42 × EER75% + 45 × EER50% + 12 × EER250%)/100
On air conditioner specification sheets, we usually get an EER rating (many times without a SEER rating). However, the EER specified on the specs is EER100%. That makes it impossible to convert from EER to SEER exactly.
Nonetheless, we can get a close estimate of what the SEER rating is from the EER ratio. For example, mini-split systems only use the SEER rating instead of the EER rating.
At EER ratings above 14, the missing measurements of EER25%, EER50%, EER75% have a much bigger impact. Therefore any EER to SEER calculation contains a potentially larger measurement error.
Nonetheless, HVAC experts from AHRI (Air-Conditioning, Heating, and Refrigeration Institute) recommend using a simple and universal formula to calculate SEER from given EER. Here’s the formula:
EER = 0.875 × SEER
Using this less-accurate but more general formula, we have created a universal EER to SEER calculator (you can see it at the beginning of this article). There you can also see SEER ratings for different EER ratings in a chart.
This EER to SEER conversion is most appropriate for below 14 EER values. For example, battery-powered air conditioners such as Zero Breeze Mark 2 have lower EER ratings (3.54 for this specific unit).
EER Below 14 (EER To SEER Calculator)
For EER up to 14, you can use a more accurate EER to SEER calculator here. Just input EER rating, and you’ll get SEER rating:
The EER to SEER calculation is based on a close approximation illustrated by the following formula:
SEER = 1.12 -1.2544-0.08×EER0.04
Here are a few examples:
- Air conditioner with an 8 EER has a 10.68 SEER rating.
- AC unit with a 10 EER rating has a 13.86 SEER rating.
- The LG LP1419IVSM portable air conditioner with a high EER rating (EER = 10.14) has a 14.04 SEER rating.
It pays to keep in mind that these calculations of SEER are based only on EER100%.
To truly calculate the SEER rating, a manufacturer has to measure EER rating at 4 different partial cooling loads, namely EER25%, EER50%, EER75%, and EER100%. Only in such a way we can calculate true SEER from EER because SEER is, in essence, a weighted average of these partial loads.